PTRPressure and Temperature Relief Valve
ECVExpansion Control Valve
TVATempering Valve Assemblies Standard
TVA – HPTempering Valve Assemblies (High Performance)
TCVTemperature Control Valve - Standard
TMVThermostatic Mixing Valve
TMV – PIBThermostatic Mixing Valve - Plumbed In Box
Hi-Flo 25Hi-Flo 25 Mixing Valve
TRI-SETTRI-SET Selectable Pressure Limiting Valve
PRVPressure Reduction Valve
NRI-PRVNon Return Isolation - Pressure Reduction Valve Combination
PRVBPressure Reduction Valve Boundary
PRVB20-BV20Boundary Pressure Reduction Valve
QPL-20Noise Reduction Valve: QPL-20
NRIBVNon Return & Isolating Valves
The Expansion Control Valve (ECV) is designed to relieve the increase in pressure caused by the water expansion during the normal heating cycle. It is recommended that an ECV be fitted to the cold water supply line. This will relieve cold water, not hot water, during the heating cycle saving energy and increasing the life of the Pressure Temperature Relief valve (PTR).
Some local governments make it mandatory to install an ECV in the cold water line. PTR and ECV valves are safety valves and should be replaced every 4 years.
Inlet Pressure Control
High pressure may cause excessive discharge and possible premature failure of the operating relief valve (see table). The maximum water pressure usually occurs during the night, at the time of lowest water usage.
In any mains pressure water heater installation if the water pressure exceeds 80% of the nominal set pressure of the operating relief valve, a Pressure Limiting Valve must be fitted to the cold inlet. If a cold water expansion control valve is fitted it will have a lower set pressure than the PTR valve and therefore will be the main operating relief valve.
|Colour Rating Plate||ECV Valves||PTR Valves|
|Blue||ECV 15/700||PTR 15/850|
Rating Plate Colours
The valve rating plates are colour coded to make selecting the correct valve easy. Simply match the EVC rating plate colour to a PTR with the same colour.